Connecting 6 or more new properties to our network.
If you are looking to connect six or more new lots, set up industrial, or large-scale commercial connections to the Counties Energy network, the following information is for you.
If you wish to connect six or fewer lots to our network, please click here.
We can offer two options to meet your requirements: a high-level assessment or a detailed design and quote. Please review the information to determine which option is relevant for you.
- A High-Level Assessment involves a desktop investigation to provide a financial estimate for budgetary purposes, this excludes a reticulation plan.
- The Customer can expect to receive this assessment 10-15 business days after receiving acknowledgment of your request.
- You can fill out the form here.
FORMAL DESIGN AND QUOTE
- A detailed reticulation plan and contract agreement will be provided with a validity of three months upon completion of the full-detail design.
- We offer Connection Design Requirements to ensure all relevant documentation is submitted for review.
- A non-refundable design fee of $5,500.00 excl GST is payable to proceed to the detailed design stage. Payment instructions will be communicated after the application is submitted.
(Note: Design fees will allow CEL to produce detailed design and price and issue a formal Contract Offer)
- Upon receiving the application and payment of the design deposit, an invoice will be issued as a receipt of payment.
- Your application will be reviewed by a Design Engineer, and you can expect to be contacted for project initiation within 10 business days.
- The expected lead time for design and quotation is subject to the complexity and will be advised when all relevant information has been reviewed. Typically, this timeframe is at a minimum 8 weeks.
- You can find the form below after accepting all terms shown.
0800 100 202
All new sub-divisions of residential lots, industrial or commercial connections as an extension onto the Counties Energy network are subject to a design and quote to provide the relevant electricity connection point(s).
Following receipt of all relevant information, the expected lead time for design and quotation is subject to complexity and will be advised once an application has been reviewed. Typically, this timeframe is at minimum 8 weeks. At the end of this design stage, you will receive a contract and associated documents. This contract would typically be valid for 3-months from the date of issue. The Customer should allow. 6 months from receiving full contract acceptance, for Counties Energy to engage a Contractor and order the required materials. Long lead time procurement is circa 7-9 months from the date of order.
The following information is required before the design can commence:
1.0 Complete the online form using the following link: https://www.countiesenergy.co.nz/forms/new-subdivision-request
2.0 Full site plan for the proposed development (or stage) in CAD format – this may include the expected Network Point of Connection location(s).
For Subdivisions, the following must be included in the CAD format site plan:
2.1. All driveway Locations – Counties Energy standard is to have a service pillar at the boundary between two properties (avoiding driveways).
2.2. All streetlight Locations – the subdivision streetlighting layout is required for the design and would ideally have approval from the relevant Local Authority.
2.3. Retaining Walls – highlight any retaining walls in the CAD file and the scheme plan in the subdivision. It will enable the designer to design efficiently to cater for service main connection(s).
2.4. All commercial Network Point of Connection location(s) – include load requirements, e.g., pump stations, traffic signal supplies, etc.
2.5. Road Back Berm detail for every road (including JOALS / ROWs) – specifically, we need to know if any proposed roads do not meet our requirement. A minimum of 600mm wide grass Back Berm (electricity cables sit within the grass Back Berm at a distance of 400mm from the property boundary).
2.6. Development/stage boundaries marked – each proposed Lot requiring a residential Network Point of Connection should be marked.
2.7. Builders Temporary Supply (BTS) – Developer/Requester to discuss the BTS requirements within the early stage of design and quote.
Note: any change to the design (including revised Lot layouts) after the application is submitted would need to be clearly defined in a revised CAD file and could be subject to a complete re-design of the entire project. The Design Engineer will confirm the effect of the design changes on the expected timeframe for the quote to be issued.
3.0 Confirmation if streetlights each have an integrated photocell sensor switch that turns them off and on based on daylight. There would be a significant additional cost if the streetlights do not have an integrated photocell sensor switch and need to be centrally controlled via a relay.
4.0 Confirmation that the developer’s appointed civil contractor will carry out all trench work within the development. It is standard for the developer’s appointed civil contractor to provide a common service trench for utilities and subsequent backfill once utilities are installed ‘within the development boundary’. The attached Subdivision HV and LV Duct & Cable Per-Section Installation requirements would form part of the contract.
- If a transformer (<1000kVA) is required for the development, a 6.3m x 4.6m set-out area, free of all other utilities, would be required. This may be via an easement if there is not enough space in the ‘to be’ vested road.
- If a HV Ring Main Unit (RMU) is required for the development, a 5.0m x 4.0m set-out area, free of all other utilities, would be required. This may be via an easement if there is not enough space in the ‘to be’ vested road.
- If both a transformer (<1000kVA) and a HV RMU are required at the same location within the development, an 9.8m x 4.6m easement/set-out area, free of all other utilities, would be required.
- All new LV connections (rated up to 160A) to Counties Energy’s network shall be made via a pillar box as per the Distribution Code.
- Supply to urban dwelling installations shall be single phase, unless otherwise agreed by Counties Energy.
- Supply to rural dwelling installations is recommended to be three phase and shall be a minimum of two phase with the connected load, balanced across all connected phases at the Main Switchboard.
Service Pillar – EP2